The Willoughby WMSII Water Management System is a PC-based water usage control network for use with Willoughby Cell Valve Controller-equipped plumbing fixtures.
By serving as the operator interface for multiple individual trunks of networked Cell Valve Controllers (CVC2), the WMSII system allows full water usage control of up to 4 networks, each with a maximum of 127 nodes connected by up to 4,000 ft. of CAT 3 network wiring, through a centrally-located PC workstation. The typical WMSII system will consist of a user-selected PC workstation, pre-programmed with a facility-specific WMSII control system; chase-mounted CVC2s, in networked or stand-alone configurations as specified; 8 ft. of CVC2-to- valve/switch wiring; and any additional support or equipment as specified. Using a WMSII system control workstation, an operator can remotely view and control any function of any networked plumbing fixture.
Each CVC2 is capable of controlling a total of 6 low-voltage solenoid valves: up to 2 lavatory/toilet combination units (1 hot valve, 1 cold valve, and 1 flush valve for each unit), 3 individual lavatories (1 hot valve and 1 cold valve each), 4 toilets with overflow sensors, 6 toilets without overflow sensors, or any other combination of 6 valves.
The Willoughby WMSII system is recommended for correctional facilities and other applications that would benefit from water conservation, usage control, and the abatement of potential vandalism. Nearly all Willoughby back-supply fixtures with an accessible mechanical chase can be networked to a WMSII system.